The Tigo Rapid Shutdown System (RSS) Transmitter is part of a rapid shutdown solution when paired with Tigo TS4-F(Fire Safety), a PV module rapid shutdown unit. While powered on, the RSS Transmitter sends a signal to the TS4-F units to keep their PV modules connected and supplying energy. TS4-F units automatically enter rapid shutdown mode when the RSS Transmitter is switched off and resume energy production when power is restored to the RSS Transmitter. This solution complies with NEC 690.12 specifications for 2014, 2017, and 2020 and uses PLC signaling for rapid shutdown. The RSS Transmitter-Commercial also includes two RSS Cores and a 480/277VAC power supply.
- Max Current: 300 Amps
- Max String Voltage: 1500 VDC
- Max Number of Strings: 10
- Max Supported PV Modules per String: 30
- Operating Temperature Range: -40°C to 85°C
- Enclosure Rating: IP68, NEMA 4
Solar Rapid Shutdown Electrical Code Requirements and Solutions
A summary of the rapid shutdown requirements for solar rooftop...
Tigo TS4 F/2F Rapid Shutdown Device Installation - TS4 Course Excerpt from Tigo Academy
This is a video excerpt from the TS4 Design and Installation C...
Tigo RSS (Rapid Shutdown System) Transmitter with Pure Signal technology
A technical summary from our training director on the features...
Tigo TS4 Flex MLPE - Product Overview
An overview of the Tigo TS4 Flex MLPE (Module Level Power Elec...