The Tigo Rapid Shutdown System (RSS) Transmitter is part of a solution for rapid shutdown. When combined with the Tigo TS4-F (Fire Safety) unit, it allows for quick shut off of PV modules in emergency situations. The RSS Transmitter sends a signal to the TS4-F units to keep them supplying energy while turned on. If the signal is lost, the TS4-F units will enter rapid shutdown mode and resume energy production when the signal is restored. This solution meets NEC 690.12 specifications for 2014, 2017, and 2020 and uses PLC signaling for rapid shutdown. The Outdoor Kit for the RSS Transmitter includes the transmitter, an outdoor enclosure, a 120/240VAC power supply, and one or two RSS Cores.
- Max Current: 150 Amps
- Max String Voltage: 1500 VDC
- Max Number of Strings: 10
- Max Supported PV Modules per String: 30
- Operating Temperature Range: -40°C to 85°C
- Enclosure Rating: IP68, NEMA 4
Solar Rapid Shutdown Electrical Code Requirements and Solutions
A summary of the rapid shutdown requirements for solar rooftop...
Tigo TS4 F/2F Rapid Shutdown Device Installation - TS4 Course Excerpt from Tigo Academy
This is a video excerpt from the TS4 Design and Installation C...
Tigo RSS (Rapid Shutdown System) Transmitter with Pure Signal technology
A technical summary from our training director on the features...
Tigo TS4 Flex MLPE - Product Overview
An overview of the Tigo TS4 Flex MLPE (Module Level Power Elec...